This new energy saving Passive Infrared wall switch utilizes an
integrated circuit manufactured with the latest surface mount technology, has
excellent detection sensitivity and a rapid response time. Its design
incorporates automatism, convenience, safety, energy-saving and practical
functions. The wide detection range senses an up, down, left and right field of
motion. It works by seeing human body heat in motion via infrared rays. It is
designed to replace an existing wall switch for interior lighting. It can start
the controlled output load (light) immediately when a person crosses the
detection field and it will not switch on unless the room is dark or dimly lit.
The unit incorporates a simple three wire installation, a status indicator LED
light and built-in photocell.
This switch controls: incandescent bulbs, LED bulbs, compact florescent bulbs (CFL) and florescent fixtures with Electronic Ballast.
The switch has 3 operating modes: AUTO, OFF and ON
Power frequency: 50~60Hz
Ambient light: Operates at less than 10 LUX
to a Maximum:7min±2min
Power source: 100V/AC~130V/AC, 220V/AC~240V/AC
1200W(220V/AC~240V/AC) - 600W(100V/AC~130V/AC)
range: 140° -> 180°
Detection distance: 9 meters maximum (29’) at less than <24°C
Working temperature:-20 to 40°C
Working humidity: Less than 93% Relative Humidity
Suggested Installation height: 1 meter to 1.6 meters ( 3’3” to 5’3”)
Detection motion speed: 0.6 to 1.5 meters
Correct the moving orientation----------- Incorrect the moving orientation
INSTALLATION: (see the following diagram)
FIRST MAKE SURE YOUR MASTER CIRCUIT BREAKER POWER IS SHUT OFF.
An Electrician should install the sensor.
Adhere to your State and Local Electrical Codes
The switch is wired across the normal Hot (Usually black –USA) and Neutral or common wire (Usually white –USA)
The sensor switch Black wire gets connected to the house Hot wire (Usually black –USA)
The sensor switch Green gets connected to the house Neutral wire (Usually white –USA)
The output light is connected to the common also and the sensor output (Red)
CONNECTION-WIRE DIAGRAM (see the right Fig)
Before installing the outer switch plate (the unit ships with the outer switch plate attached, you must remove it), lift off the time-delay adjustment access panel. To do this, place a small flat screwdriver in the small notch directly below the detection window and gently pry the removable panel down and out. Behind this panel you will see the time-delay adjustment dial. Turn the time-delay dial counterclockwise to the minimum. (It may be at the minimum already). After first applying power, the controlled load (light bulb) won’t work and the indicator lamp flashes slowly (one time every 4 seconds). The load should work within 10 seconds and the indication lamp will start to flash fast (2 times every 1 second). Move out of range and allow the light to go off. (This should happen within about 5 to 30 seconds). At this point the LED indicator will start to flash slowly again. Move into the detection area and the lights should work and the indicator LED should start to flash rapidly again.
1. In the
case where the light connected to the sensor won’t switch on:
a. If the LED flashes fast after detecting movement, please check if the switch is on the "auto" position.
b. If the LED light is flashing check the load (light) or the switch connections, if the LED light is not flashing at all please check the power, the main fuse or circuit breaker.
d. Please check if the room lighting is low level and within the 10 LUX threshold.
2. In the case that the sensitivity is poor:
a. Please check if the front of the detection window is somehow blocked.
b. Please check the ambient temperature.
c. Please check if the movement source is within range of the sensor.
d. Please check the installation height.
e. Please check if the direction of movement is perpendicular to the sensor switch.
3. In the case where the output load will not shut off:
a. Please check if there is anything emitting heat and also moving air in the detection field.
b. Pleased check the time delay relative to the last detected motion within range.
c. Please ensure that the power is within the operating range.
e. Mirrors can reflect motion in the sensor view, check to see if the sensor is facing a mirror and if the mirror is facing some moving warm object.